(b) Definition. -- For the purposes of this section, the term "bed and breakfast establishment" means a building occupied as a one-family dwelling unit that provides sleeping accommodations and breakfast to transient guests for a single fee and does not offer more than six guest rooms to no more than twelve guests.
(c) Fire code standards. -- Notwithstanding any provision of this code to the contrary, every bed and breakfast establishment shall be exempt from provisions of fire safety code requirements which are contrary to the following standards:
(1) Each bed and breakfast shall have operational smoke alarms in all common areas, guest rooms and hallways and heat detectors as otherwise required by this code or rule of the Fire Commission. Battery-powered smoke alarms shall be permitted where the establishment has demonstrated that the testing, maintenance and battery replacement procedures will ensure reliable power to the smoke alarms. Notwithstanding any provision of this code to the contrary, no smoking will be allowed inside a bed and breakfast establishment.
(2) Each bed and breakfast shall have operational hard-wired, battery-powered or plug-in emergency lighting that indicate available means of egress. Battery-powered or plug-in emergency lighting devices shall be permitted where the establishment has demonstrated that the testing, maintenance and battery replacement procedures will ensure reliable power to the emergency lighting devices.
(3) Each guest floor shall have a primary and a secondary means of egress. A door leading directly from a guestroom outside the building with access to grade, or a stairway which is covered or enclosed, or a covered balcony or deck with a stairway to grade are acceptable secondary means of egress. A bed and breakfast with third-floor guest rooms must have an accessible second stairway leading from the third floor to grade. Any bed and breakfast establishment with a sprinkler system which otherwise meets the requirements of this section and the state fire safety and building codes is exempt from the requirement of a secondary means of egress. A bed and breakfast establishment which offers three or fewer guest rooms on the first or second floor only, and accommodates no more than six guest occupants at one time, is exempted from the secondary means of egress requirement;
(4) The state Fire Commission shall permit bed and breakfast establishments that cannot readily comply with the requirements of a legislative rule, which may mandate the installation of a secondary means of escape or a sprinkler system, one year per floor of the establishment to comply with the requirements.
(5) All other provisions of the state fire safety code not inconsistent with this section and rules promulgated pursuant to subsection (d) of this section are applicable to bed and breakfast establishments.
(d) Legislative rules. -- The state Fire Commission shall promulgate or amend an existing legislative rule, in accordance with the provisions of article three, chapter twenty-nine-a of this code, to effectuate the provisions of this section. The rule shall include a mechanism for the Fire Commission to grant individual variances to bed and breakfast establishments which cannot otherwise meet provisions of the state fire safety code due to the historic and architectural significance of the establishment with due consideration of the economic limitations inherent in the operation of this type of small business.
(e) Historic preservation review. -- The owner of a bed and breakfast may request the historical preservation section of the Division of Culture and History, pursuant to section eight, article one of this chapter, to consult with the owner and provide a recommendation to the Fire Commission regarding the historic character of the structures used or proposed to be used as a bed and breakfast and any objections or concerns regarding any renovations or other changes required by the Fire Commission or Fire Marshal. If an appeal regarding a decision made by the Fire Marshal is made to the Commission as provided by section eighteen of this article, the Commission shall consider the recommendation of the historical preservation section when making a determination regarding the variance as provided for in subsection (d) of this section.
Note: WV Code updated with legislation passed through the 2016 Regular Session
The West Virginia Code Online is an unofficial copy of the annotated WV Code, provided as a convenience. It has NOT been edited for publication, and is not in any way official or authoritative.